Compliance Statements for NEBS Standards for JSA7500
JSA7500 complies with the following Network Equipment Building System (NEBS) standards:
GR-1089-Core: EMC and Electrical Safety for Network Telecommunications Equipment.
The equipment is suitable for installation as part of the Common Bonding Network (CBN).
The equipment is suitable for installation in locations where the National Electrical Code (NEC) applies.
The battery return connection is to be treated as an isolated DC return (that is, DC-I) as defined in GR-1089-CORE.
The intrabuilding port(s) (40G DACS and USB ports) of the equipment or subassembly must use shielded intrabuilding cabling/wiring that is grounded at both ends.