The following electrical safety guidelines apply to a DC-powered services gateway:
A DC-powered services gateway is equipped with a DC terminal
block that is rated for the power requirements of a maximally configured services gateway.
To supply sufficient power, terminate the DC input wiring on a facility
DC source capable of supplying at least 58 A (32 A per feed) @ –48 VDC for the system. We
recommend that the 48 VDC facility DC source be equipped with
a circuit breaker rated at 125% of the power provisioned for the input minimum,
or as required by local code. Incorporate an easily accessible disconnect
device into the facility wiring. In the United States and Canada,
the –48 VDC facility should be equipped with a circuit
breaker rated a minimum of 125% of the power provisioned for the input
in accordance with the National Electrical Code in the US and the
Canadian Electrical Code in Canada. Be sure to connect the ground
wire or conduit to a solid office (earth) ground. A closed loop ring
is recommended for terminating the ground conductor at the ground
Run two wires from the circuit breaker box to a source
of 48 VDC. Use appropriate gauge wire to handle up to 50 A.
A DC-powered services gateway that is equipped with a DC
terminal block is intended only for installation in a restricted access
location. In the United States, a restricted access area is one in
accordance with Articles 110-16, 110-17, and 110-18 of the National
Electrical Code ANSI/NFPA 70.
Primary overcurrent protection is provided by the building circuit
breaker. This breaker should protect against excess currents, short
circuits, and earth faults in accordance with NEC ANSI/NFPA70.
Ensure that the polarity of the DC input wiring is correct.
Under certain conditions, connections with reversed polarity might
trip the primary circuit breaker or damage the equipment.
For personal safety, connect the green and yellow wire
to safety (earth) ground at both the services gateway and the supply
side of the DC wiring.
The marked input voltage of –48 VDC for a DC-powered services gateway is
the nominal voltage associated with the battery circuit, and any higher
voltages are only to be associated with float voltages for the charging
Because the services gateway is a positive ground system,
you must connect the positive lead to the terminal labeled RETURN, the negative lead to the terminal labeled –48V,
and the earth ground to the chassis grounding points.