Preparing the SRX300 Services Gateway for Rack-Mount Installation
You can mount an SRX300 Services Gateway in four-post (telco) racks, enclosed cabinets, and open-frame racks.
The SRX300 Services Gateway cannot be center-mounted in racks.
Before mounting the SRX300 Services Gateway in a rack:
Verify that the installation site meets the requirements described in Site Preparation Checklist for the SRX300 Services Gateway.
Verify that the racks or cabinets meet the specific requirements described in SRX300 Services Gateway Rack-Mounting Requirements and Warnings.
Place the rack or cabinet in its permanent location, allowing adequate clearance for airflow and maintenance, and secure it to the building structure. For more information, see SRX300 Services Gateway Clearance Requirements for Airflow and Hardware Maintenance.
Remove the services gateway chassis from the shipping carton. For unpacking instructions, see Unpacking the SRX300 Services Gateway.
Verify that you have the following parts available in your rack-mounting kit:
The rack-mounting kit is not shipped with the device and must be ordered separately.